Shipping 0,00 €
Tax 0,00 €
Total 0,00 €
Prices are tax included
Welcome Log in
You install behind every solar panel. You have an excellent and proposition with regard to the centralized solar inverters.
This solar micro-inverter ENPHASE optimizes you in a significant way the power production, decreases the exposure time and insures a follow-up 24 hours on 24 of each your solar panels. You thus make sure an optimization of the performance of solar plan.
The 25 years ENPHASE solar micro-inverter warranty insures you a quality of return throughout the life cycle of your solar panels. No many who can aspire to a solar performance on all this duration.
The communication is equal a strength at ENPHASE. All the solar micro-inverters are linked with internet by carrier current. The interface of ENPHASE is simple and fast of use.
The Enphase Energy Micro-inverter System improves energy harvest, increases reliability, and dramatically simplifies design, installation and management of solar power systems.
The Enphase System includes the microinverter, the Envoy Communications Gateway, and Enlighten, Enphase’s monitoring and analysis software.
ENPHASE solar micro-inverter is based on PLUG AND PLAY. Try it is to adopt it.
The Engage Cable is a continuous length of 2.5 mm2, outdoor rated cable with integrated connectors for microinverters. These connectors are preinstalled along the Engage Cable at intervals to accommodate PV module widths. The microinverters plug directly into the connectors, and the Engage Cable is terminated into the junction box that feeds electricity back to the system AC disconnect.
|||Lay the Engage Cable along the route it will travel, positioning the connectors so that they align with the solar panels.|
Mark the approximate centres of each PV module on the mounting rail. Evaluate the location of the microinverter with respect to the PV module DC junction box or any other obstructions. Allow a minimum of 1.9 cm (0.75 inches) between the roof and the bottom of the microinverter. Also allow 1.3 cm (0.50 inches) between the back of the PV module and the top of the microinverter. With the silver side of the microinverter facing up and the black side facing down, mount one microinverter at each location using suitable hardware. The indicator light on the underside of the microinverter will be facing the roof.
Remove and discard the temporary shipping cap from the Engage Cable and connect the micro inverter. There are two latching mechanisms within the connectors. Listen for two clicks as the connectors engage. Ensure that both latching mechanisms have engaged.
Repeat for all microinverters in the AC branch circuit.
|||Cover any unused connector with a sealing cap. Listen for two clicks as the connectors engage. Ensure that both latching mechanisms have engaged.|
Remove 60mm (2.5 inches) of the cable sheath from the conductors. Slide the hex nut onto the Engage Cable. Insert the Engage Cable all the way into the wire organiser (up to the stop). Bend the individual wires back into the recesses in the wire organiser so that they angle back toward the cable.
Screw the hex nut onto the cap. Never unscrew the hex nut as this can twist and damage the cable. Ensure that all cabling is located underneath the PV module.
|||Connect Engage Cable into the AC branch circuit junction box using an appropriate gland or strain relief fitting. The Engage Cable requires a strain relief connector with an opening of 1.3 cm (0.5 inches) in diameter. Connect the Engage Cable into additional AC junction boxes as needed to transition to conduit between smaller sub-arrays.|
|||Mount the PV modules above the microinverters. Mate the microinverters and PV modules as required. Repeat for all remaining PV modules using one microinverter for each PV module.|